We've got you covered!
3X4 Flange adaptor
4X3 Flange adaptor
4X4 Flange adaptor
4X6 Flange adaptor
6X4 Flange adaptor
2" Flygt rail adaptor
2" FRA w/ 3" flange
3" Flygt rail adaptor
3" ANSI modified to JIS
4" Flygt rail adaptor
4" ANSI modified to JIS
6" Flygt rail adaptor
6"ANSI modified to JIS
6"Modified for 3 inch guide rails
We can slide any pump down any rail system!
Custom made flanges ensure a perfect fit every time so you don't have to worry about installation issues.
"Serving the industrial and municipal water and wastewater community since 1995"
2" ELBOW Flange with 2” NPT Threads
3"ELBOW Flange with 3” NPT Threads
4" ELBOW FL by FL or 4" NPT Threads
6" ELBOW FL by FL or 6" NPT Threads
8" ELBOW FL by FL
RENTAL FLEET - From 3-50 HP, we have you covered while your pump is being repaired!
Included with Adaptor Flanges: Stainless Steel Studs and Nuts for mounting to the Pump
Instructions: With an ANSI Flange on the Pump you can bolt on a rail adaptor and slide the pump down an existing guide rail system.
Flygt Installation: Flygt Guide Rail Adaptor to be bolted on the Adaptor Flange. Flygt Guide Rail Adaptors have an ANSI bolt pattern unless listed with an “M” at the end of the p/n.
Bolt Patterns: 4” JIS Bolt Pattern is 2.625” bolt hole center. 3” JIS Bolt Pattern is 2” bolt hole center.
Instructions: Most Hydromatic, Barnes, Myers Pumps have an ANSI Flange on the volute and use a bolt on the rail adaptor. This existing rail adaptor can be reused on the flange adaptor to install a Pump on the existing guide rail system.
Example: Pump to be replaced: Flygt model 3152 w/432 impeller 6” volute. Notice: some Flygt pumps are available with 2 different discharge sizes. In this case 6”or 8”. In this particular case it is 6”
Replaced with Pump Model 100C415 - Volute Flange Size is 4” JIS
Note: This would require a 4 x 6 flange adaptor and 6” Flygt Rail Adaptor. Both flange adaptor and Flygt Rail Adaptor are required.